AURORA 255760 LOGIX-15M – MONOBLOCK 15LT WATER SOFTENER
Aquatekna water softening systems are designed to maximize water quality in homes, hotels, restaurants, industrial facilities. Hard water is very common in many areas. Hard water causes scale to form in pipes, plumbing fixtures, kitchen appliances as well as in coffee machines, ice machines, boilers and dish washers in professional installations.
Soap reacts with hard water to form a curd, and hard water can also cause skin flaking and irritation. More soap or detergent is needed when washing or laundering with hard water. Hardness is primarily caused by the dissolved chemical compounds of calcium and magnesium. The amount of hardness is expressed in milligrams per litre (mg/L) or as French or German Degrees.
Water softeners operate on the principle of ion exchange. A synthetic resin (zeolite) bed is charged with sodium ions by regeneration with salt (sodium chloride). Hard water, containing calcium and magnesium ions, flows through the resin. Ion exchange occurs when the calcium and magnesium ions attach themselves to the resin, displacing the sodium ions. The resultant water is softened, being free from calcium and magnesium.
In this Aurora 255-760LOGIX 15M softening system, we use the tried and tested General Electric Autotrol 255-760 valve from Pentair USA, which is fully programmable and has both volumetric and chronometric functions available. This gives the system top performance and guaranteed operation during regeneration, in a fully automated domestic water softener.
The hardness of the incoming water is programmed in the electronic memory of the valve, together with the capacity of the resin tank and the valve automatically calculates how many liters of water can be processed.
The valve measures the amount of water that passes through the resin tank and starts the regeneration process when its capacity is exhausted. This particular Autotrol 255-760 valve can also be programmed for timer regeneration, ie it can be programmed to regenerate every 1, 2, 3, or 6 days, or as often as we like, depending on the memory setting in the valve.
Up to 3 mg/L of iron can readily be removed with our five cycle fully automatic softener. If the water supply contains iron, a sodium hydrosulphite resin cleaner should be used regularly according to the manufacturer’s instructions. If the iron is not cleaned from the softener, its capacity will be drastically reduced.